Construction of Vertical Sump Pump
Main Part With Numbers In The Drawing
1. Shaft 2. Dust Cover 3. Bearing 4.Bearing Gear Sleeve 5. Bearing Body 6. Bearing 7. Bracket 8. Filter Net 9. Rear Guard Plate 10. Impeller 11. Pump Body 12. Lower Filter 13. Spit Tube 14. Split Spout Flange 15. Bearing Gland
VERTICAL SUMP PUMP SELECTION CHART
Note: Approximate Performance For Clear Water, To Be Used For Primary Selection Only.
√ Bearing Assembly – The bearings, shaft and housing are generously proportioned to avoid problems associated with the operation of cantilevered shafts in the first critical speed zones.
The assembly is grease lubricated and sealed by labyrinths; the upper is grease purged and the lower protected by a special flinger. The upper or drive end bearing is a parallel roller type whilst the lower bearing is a double taper roller with preset end float. This high performance bearing arrangement and robust shaft eliminates the need for a lower submerged bearing.
√ Column Assembly – Completely fabricated from mild steel. The SPR model is elastomer covered.
√ Casing – Has a simple bolt-on attachment to the base of the column. It is manufactured from a wear resistant alloy for the SP and from moulded elastomer for the SPR.
√ Impeller – Double suction impellers (top and bottom entry) induce low axial bearing loads and have heavy deep vanes for maximum wear resistance and for handling large solids. Wear resistant alloys, polyurethane and moulded elastomer impellers are interchangeable. The impeller is adjusted axially within the casting during assembly by external shims under the bearing housing feet. No further adjustment is necessary.
√ Upper Strainer – Drop-in metal mesh; snap-on elastomer or polyurethane for SP and SPR pumps. Strainers fit in column openings.
√ Lower Strainer – Bolted metal or polyurethane for SP; moulded snap-on elastomer for SPR.
√ Discharge Pipe – Metal for SP; elastomer covered for SPR. All wetted metal parts are completely rust protected.
√ Submerged Bearings – None
√ Agitation – An external agitator spray connection arrangement can be fitted to the pump as an option. Alternatively, a mechanical agitator is fitted to an extended shaft protruding from the impeller eye.
√ Materials – Pumps can be manufactured in abrasive and corrosive resistant materials.
Clear Water Performance